DUPONT R134A PH DIAGRAM FILETYPE PDF
DuPont Freon 12 Saturation Properties Temperature reading comprehension thermodynamic propertiesFigure A14 P-h diagram for refrigeranta. manual describes the version of EES developed for Microsoft Windows operating systems, including .. format. The first argument of the function is the substance name, Ra in this case. The PropPlot %%1 PH 2 %%2 %%3 0 DoQLines automatically determine the file type independent of the filename extension. mollier chart for thermal engineering if looking for the ebook by mollier chart for free pdf download mollier free thermal engineering rs khurmi file type pdf table mollier . replacement for ra in refrigeration applications thomas j leck dupont.
|Published (Last):||27 January 2009|
|PDF File Size:||11.87 Mb|
|ePub File Size:||4.48 Mb|
|Price:||Free* [*Free Regsitration Required]|
On the P-H diagram, pressure is indicated on the y-axis and enthalpy is indicated on the x-axis.
The upside down U figure shown on the diagram designates the points at which the refrigerant changes phase. The left vertical curve indicates the saturated liquid curve and the right vertical curve indicates the saturated vapor curve. The region in between the two curves describe refrigerant states that contain a mixture of both liquid and vapor. The locations to the left of the saturated liquid curve indicate that the refrigerant is in liquid form and locations to the right of the saturated vapor curve indicate that the refrigerant is in vapor form.
The point at which the two curves meet is called the critical point. The importance of this point is that at any point above, no additional pressure will change the vapor into a liquid. A simplified pressure-enthalpy diagram is shown below, describing this information. The liquid region is also known as the sub-cooled region. In this region there are vertical temperature lines, which increase as enthalpy is increased.
Pressure Enthalpy Diagram
Figure 8 is a simplified P-H diagram illustrating the constant temperature lines. The vapor region is also known as the super heated region. Refer to Figure 8. There are also lines of constant entropy, which are also important. Entropy is the measure of the amount of disorder in the system. In this region, the P-H diagram shows horizontal temperature lines, which indicate constant temperature.
The mix region is the phase change region, where any addition of enthalpy will cause additional liquid to r314a instead of raising the temperature. Figure 8 illustrates the horizontal temperature lines in the mix region.
Refrigerant R12 properties
There are also upward sloping curves which indicate quality. Quality is a measure of the ratio of vapor mass to total mass. For example quality of 0.
The previous figure, Figure 7, indicates the quality lines. The x-y axes of the P-H diagram are the pressure lines running from left to right.
The enthalpy lines are the vertical lines. The skeletal graph shown below shows the pressure-enthalpy lines. One of the most important skills needed for the professional engineer in the HVAC and Refrigeration field is navigating the refrigeration cycle on a pressure-enthalpy diagram.
The following sections will show each specific part of the refrigeration cycle on the pressure-enthalpy diagram and it will also highlight the important points and calculations needed.
Throughout this explanation the refrigerant Ra is used as an example. It is recommended that the engineer get a diavram of the P-H diagram for Ra and the diafram common refrigerants. The refrigerant entering the evaporator is a cold, partial liquid-vapor mixture. The operating pressure and temperature of the evaporator is called the suction pressure and suction temperature.
The suction line is the piping that routes refrigerant gas from the evaporator to the compressor.
It is important to note that in the mix region, the pressure and temperature are dependent variables. For example, if a compressor operates at a suction pressure of If the compressor operates at a suction pressure of The evaporator moves the refrigerant from point A partial liquid-vapor mixture to point B, a fully saturated vapor refrigerant.
As the evaporator transfers heat to the refrigerant, there is no gain in temperature, since all the heat is used to convert the remaining liquid to a gas. In an ideal evaporator, there is just enough heat transfer to convert all the liquid to gas and nothing more. Also introduced in the figure above is the term superheat.
Refrigerant R12 properties
It is important to note that the pressure remains constant throughout the evaporator. The compressor is characterized by the refrigerant suction and discharge conditions. Horizontal lines are drawn across the refrigerant’s pressure enthalpy diagram for the suction and discharge pressures. Then the incoming temperature of the compressor, as determined by the leaving temperature of the evaporator, is used as the starting point of the compressor, as shown by point B’ on the figure below.
The compressor then increases the pressure of the refrigerant up to the discharge pressure. Compression occurs at constant entropy, also known as isentropic compression.
Therefore the intersection of the constant entropy line and the discharge pressure line will identify the final condition of the refrigerant gas leaving the compressor, as shown by point C’ in the figure below. A common skill, that is required of a professional engineer, is to determine the work done by the compressor.
This work is shown in the figure above as the difference between the compressor entering enthalpy H1 and the leaving enthalpy H2. The equation to determine the work of the compressor is shown below. This equation multiples the refrigeration flow rate by the change in enthalpy between the discharge and suction conditions. The refrigerant entering the condenser is now a hot, high pressure refrigerant gas.
The condenser is shown on the pressure-enthalpy diagram as a horizontal line. This horizontal line is a line of constant pressure, corresponding to the discharge pressure of the compressor. The condenser proceeds from right to left in the following three steps:. Cooling takes place as heat flows from the hot refrigerant gas to the condenser cooling medium.
Heat is lost to the condenser cooling medium as the vapor is condensed to a liquid. In an ideal condenser, no sub-cooling occurs.
Once the refrigerant is a fully saturated liquid, any additional heat loss results in a decrease in temperature. This cooling of the saturated liquid is referred to as sub-cooling.
A common question is to determine the heat expelled by the condenser, which is shown in the figure above as the difference between the condenser entering condition H2 and the leaving condition H4.
The equation to determine the net condenser effect is shown below. This equation multiples the refrigeration flow rate by the change in enthalpy between the entrance and exit of the condenser. The expansion device is the counterpart of the compressor. Similarly, the expansion device is characterized by the suction and discharge pressures. Horizontal lines are again drawn on the refrigerant’s pressure-enthalpy diagram. The input condition of the expansion device is determined by the condenser output conditions.
There are two entering conditions to the expansion device shown on the following diagram. The expansion device expands the high pressure refrigerant gas adiabatically to a low pressure liquid-vapor refrigerant mixture. Adiabatic expansion indicates that there is no change in enthalpy and is characterized by a downward vertical line as shown on the below graph.
Note on the graph below as the refrigerant moves from point D to point A, the refrigerant moves from the liquid phase of the graph to the vapor-liquid mixture region. The amount of gas that is formed during this expansion is called flash gas. Pressure Enthalpy Diagram This diagram describes the relationship of pressure and enthalpy of a select refrigerant. In order to properly understand this diagram, it is best to go through the vapor compression cycle on a P-H diagram.
Understanding the P-H Diagram On the P-H diagram, pressure is indicated on the y-axis and enthalpy is indicated on the x-axis. The curves break up the diagram into three regions 1 Liquid, 2 Vapor and 3 Mix. Refrigeration Cycle One of the most important skills needed for the professional engineer in the HVAC and Refrigeration field is navigating the refrigeration cycle on a pressure-enthalpy diagram.
The condenser proceeds from right to left in the following three steps: Learn what resources you need at a minimum to pass the PE exam.